Manufacturer: Schneider Electric USA Inc
Product: Square D branded, molded case F and K frame circuit breakers
Hazard: The circuit breaker can fail to trip when an overload occurs, posing the risk of fire, burn and electric shock.
Injuries: None reported.
Description: This recall involves Square D brand models FA, FH, FI and FY one-, two- and three-pole circuit breakers rated 15 to 100 amps, and model KI two- and three-pole circuit breakers rated 110 to 250 amps. The F model breakers were manufactured May 8, 2013 through June 10, 2013 and have date codes 13193 through 13241. The K models were manufactured May 2, 2013 through June 21, 2013 and have date codes 13184 through 13255. The date codes are YYWWD format (example: 13184 = year 2013, week 18, day of the work week 4/ Thursday). The circuit breakers have a yellow label with the words “Square D” or the Square D logo. Model information can be found on the faceplate.
Sold At: Authorized Schneider Electric distributors nationwide such as Border States Electric Supply, Crescent Electric Supply Co., Dealers Electric Supply Co., Graybar Electric Co., Rexel, W.W. Grainger from May 2013 to June 2013 for between $200 and $9,260.
Units: About 28,400
Consumer Contact: Schneider Electric USA at (800) 634-8730 anytime. Consumers can also visit the firm’s website at www.schneider-electric.us and click on “customer notification” under the popular links category for more information.